Wiring / Connecting 2 Wire and 4 Wire Smoke Detectors to an Alarm System
We are often asked how to connect low voltage smoke detectors to a wired alarm system. First we need to point out that smoke detectors are a life safety product and so it's critical that you read and understand how the connection should work, and hire a pro if needed. You will also need to test the after installation and regularly thereafter to ensure they are working.
There are two types of low voltage smoke detectors: 2 wire and 4 wire smoke detectors. A 2 wire smoke detector will typically connect to a special two wire FIRE zone on the panel with only 2 wires. Multiple smoke detectors can be connected. A 4 wire smoke detector can typically connect to any wired zone, and the zone needs to be specified in panel programming as a fire zone. More often, each 4-wire detector goes on its own zone, which aids in determining exactly which detector was triggered, but it's possible to connect more than one.
Also an EOL (end of line) resistor is normally required to be installed at the - end of the line at the (last) smoke detector. An end of line relay may also be required to supervise power on a 4 wire connection.
Again, if in doubt please hire a pro to make sure it's done safely.. it's there to protect your life & property after all. We will not provide detailed instructions beyond this basic information. We recommend this work to be completed by a pro.
SAMPLE TWO WIRE SMOKE DETECTOR CONNECTION
SAMPLE 4 WIRE SMOKE DETECTOR CONNECTION
Add existing wired smoke detectors to a DSC alarm system
We are often asked how to add existing smoke detectors to a DSC alarm system. There are 3 options we can suggest: Install DSC wireless smoke detectors separately so they don't interfere with your current system. This has the benefit of having each ...
Troubleshooting a Beeping or Chirping Smoke Detector or Carbon Monoxide Detector
If your smoke detector or carbon monoxide detector is sounding an alarm, you need to take action immediately to check for smoke or in the case of a carbon monoxide alarm clear the building and call the fire department to check for dangerous CO ...
Connecting 2012JA 4 Wire Smoke Detector
For liability and safety reasons we can't provide advice or direction related to your specific panel or installation, however we can provide some general guidance: Power Input will connect to the power output of the panel, possibly an aux out, that ...
Difference Between 2 Wire and 4 Wire Smoke Detector for Alarm System
Your home or business alarm system protects both from intrusion, but often uses smoke detectors to provide protection against fire. For low voltage alarm system smoke detectors, there are two basic wiring types. 2 Wire Smoke Detectors and 4 Wire ...
Replace 330L smoke detector
> My home has smoke alarm installed by builder in 1990. There are 3 alarms > which I believed are connected together. The model is Dicon 330L which I > believed is no longer available by searching the internet. And, they > recommended to search your ...