Simply Automated V-3Way Wiring and Troubleshooting
> - Do you have proper schematics when more than one pair of switches are installed?
> - What exactly is the wire that is white with a brown stripe supposed to be for?
> - Is the brown wire required on both switches of a pair in each room?
These are virtual switches. Both switches need full time power - neutral connection, typically white, hot (black wire on switch) must have power all the time and not be switched by anything else. The brown wire is the 'load' wire and is the one that 'powers' the light you are trying to control. In the case of a virtual three way, one of the switches needs to be connected to the load/light via the brown wire. The other one would have the brown wire capped off.
Based on that the wiring is going to be the same regardless of how many of these pairs you put on a circuit, always neutral to neutral, hot to hot, brown from one switch to the load/light you're controlling.
If the LEDs themselves are not behaving as expected, it could be a programming/pairing issue, please contact www.simply-automated.com support.
If the switches are reacting but the physical light you are trying to control is not working, it could be that there is a wiring problem.
If one switch goes dead when the other goes off, that's definitely a wiring problem.
Troubleshooting Zwave Lock Installation
Zwave locks are one of the most finicky Zwave devices to enroll in to an automation system because they use Zwave security transmission and initially create a large amount of 'data' back and forth while the lock is being enrolled. Here are some ...
Insteon with Aluminum Wiring
Aluminum wiring is less conductive then copper so the INSTEON signal may be slightly affected by that but the signal can go a long way on the powerline so the aluminum wiring does not have a major effect in a residential home. Where it can be ...
INSTEON Switches or Dimmers in 3 Way and 4 Way Circuits
For a 3 way (2 switches) or 4 way (3 switches) circuit, you need to replace both/all switches with INSTEON switches. The master switch that controls the load can be a dimmer, relay switch or keypad. The remote switches(s) can be keypad or similar ...
Wiring and Cabling Considerations for a New Home or Renovation
While building you're best to put in more wire than you think! CAT5E is your friend for many applications including networking, telephone, whole home audio, intercoms and more. You may want to consider lighting control wiring (120V electrical), ...
INSTEON and Automated Switches on GFCI Protected Circuits
Circuites with panel mounted GFCI circuit breakers, particular older models, can falsely trip when there is an INSTEON dimmer or automated dimmer on the circuit. 1) checking for loose wiring and neutrals (you'd be surprised), at both switch and ...